Electronics densification in head ends, hubs or other aggregation points is driving the need for increased space inside existing buildings, shelters, huts, etc. Holland Electronics 2V Battery Enclosures allow operators to recover valuable, conditioned space within existing buildings by enabling the movement of large 2V strings to the outside of buildings. The battery strings can be disconnected and moved with minimal or no disruption to the network. When faced with the choice between a costly building expansion versus deployment of an enclosure outside the building, the choice is simple – Holland Electronics 2V Battery Enclosure solution saves operators money!
CUBE Battery Backup (BBU) cabinets are ideally suited for head ends, hub sites, cell sites and other outdoor environments when a large amount of battery backup is required. Multiple BBU cabinets can be combined to achieve an even greater amount of battery backup time or string redundancy. BBU cabinets can be installed adjacent to or remotely from other CUBE Site Support (CUBE-SS) Power Enclosures.
Construction: 0.125″ Aluminum Welded Construction Outer Enclosure, Powder Coated Cool White Finish
Mounting Style: Pad Mount Enclosure
Thermal Management: Solar Shield and Venting on all models, Direct Air Cooling, DC HVAC or AC HVAC for Env. Conditioning
Door Latching: 3-Point Latching with Pad Lockable Handle in Front, Removable Panels in Rear, Wind Latch Each Door
Battery Types: 2V VRLA Strings
Battery Breakers: Optional 1200A Disconnect available as add on kit
Cable Entrance: Eight .5” Knockouts on rear serve as centering points for Greenlee punch to support larger conduits
Alarms: Door Intrusion, High Temperature, HVAC Failure (on configurations with HVAC)